CyberPower UPS - ArchWiki

# CyberPower UPS

This document describes how to install the CyberPower UPS daemon or alternatively the Network-UPS-Tools. The main advantage of using a CyberPower UPS is that it is cheap and it can communicate with your Linux box through either a RS-232 or USB serial connection. In the event of a prolonged power outage, should the CyberPower UPS lose most of its battery capacity, it can tell the Linux box to perform a safe shutdown.

## Installation of Power Panel

Install powerpanel (powerpanelAUR) from AUR.

### Configuration

Edit `/etc/pwrstatd.conf`

Email notifications can be accomplished by editing `/etc/powerpanel/pwrstatd-powerfail.sh` and `/etc/powerpanel/pwrstatd-lowbatt.sh`

Warning: Make sure the path to the email script at the bottom of these scripts is correct. It should be `/etc/powerpanel/pwrstatd-email.sh`

### Running

Start and enable the service

    # systemctl start pwrstatd
    # systemctl enable pwrstatd

Then run `# pwrstat -status`

You should get something like this:

    The UPS information shows as following:

            Properties:
                    Model Name...................  Value 1500E
                    Firmware Number.............. BFF7104#7N5
                    Rating Voltage............... 230 V
                    Rating Power................. 900 Watt

            Current UPS status:
                    State........................ Normal
                    Power Supply by.............. Utility Power
                    Utility Voltage.............. 230 V
                    Output Voltage............... 230 V
                    Battery Capacity............. 100 %
                    Remaining Runtime............ 61 min.
                    Load......................... 126 Watt(14 %)
                    Line Interaction............. None
                    Test Result.................. Unknown
                    Last Power Event............. None

## Installation of Network UPS Tools

If you do not wish to use powerpanel, the Network UPS Tools (NUT) offers an alternative for some UPS; not all are supported. It's worth checking the Hardware Compatibility List to see if your UPS is supported. Only one of these programs is required to monitor and shut the system down; you shouldn't use both as they might interfere with one another.

You can install network-ups-tools (network-ups-toolsAUR) from AUR.

### Configuration

NUT has 3 daemons associated with it:

- The driver which communicates with the UPS
- A server (upsd) which uses the driver to report out the status of the UPS
- And a monitoring daemon (upsmon) which monitors the upsd server and takes action based on information it receives.

The idea is that if you have multiple systems connected to the UPS, one can communicate the status of the UPS over the network and the others can monitor that status by running their own upsmon services. NUT has extensive documentation on the configuration however this is going to walk through a simple setup of a USB UPS and the associated server and monitor all in one system (common desktop configuration).

#### Driver Configuration

Edit `/etc/ups/ups.conf`

The configuration here will depend on the type of UPS you have. For a simple usb-hid compatible UPS:

    [powerplant]
        driver = usbhid-ups
        port = auto

That creates a new UPS called "powerplant". You can name the device whatever you like. If you don't have a usbhid-ups, the previously mentioned Hardware Compatibility List may help, or you can run the "nut-scanner" command which may be able to poll the system for attached UPS.

#### upsd Configuration

Optionally Edit `/etc/ups/upsd.conf`

Then Edit `/etc/ups/upsd.users`

The default upsd.conf will work. It is configured by default to only listen on localhost so if you ever wish to add network monitors, you will need to adjust this file. For our basic configuration though, this will work fine.

upsd.users however needs to be configured with a user so we can issue commands to the server and monitor it. You should populate it with a user and password.

    [scottie]
         password = warpspeed
         actions = SET
         instcmds = ALL

At this point you should be able to start up nut-server (which will automatically start nut-driver).

    # systemctl start nut-server
    # systemctl enable nut-server

If it has started successfully, you can run upsc <upsname> to get info from the ups. Example output would be:

    battery.charge: 100
    battery.charge.low: 10
    battery.charge.warning: 20
    battery.mfr.date: CPS
    battery.runtime: 5550
    battery.runtime.low: 300
    battery.type: PbAcid
    battery.voltage: 13.5
    battery.voltage.nominal: 12
    device.mfr: CPS
    device.model: UPS CP1000AVRLCD
    device.type: ups
    driver.name: usbhid-ups
    driver.parameter.pollfreq: 30
    driver.parameter.pollinterval: 2
    driver.parameter.port: auto
    driver.parameter.synchronous: no
    driver.version: 2.7.4
    driver.version.data: CyberPower HID 0.4
    driver.version.internal: 0.41
    input.transfer.high: 140
    input.transfer.low: 90
    input.voltage: 122.0
    input.voltage.nominal: 120
    output.voltage: 122.0
    ups.beeper.status: disabled
    ups.delay.shutdown: 20
    ups.delay.start: 30
    ups.load: 0
    ups.mfr: CPS
    ups.model: UPS CP1000AVRLCD
    ups.productid: 0501
    ups.realpower.nominal: 600
    ups.status: OL
    ups.test.result: Done and passed
    ups.timer.shutdown: -60
    ups.timer.start: 0
    ups.vendorid: 0764

#### upsmon Configuration

The last step is to configure upsmon to listen to upsd and take action. At least one line is needed to configure upsmon to log in with the username and password you set in upsd.users.

    MONITOR powerplant@localhost 1 scottie warpspeed master

The file also configures what alerts are sent and where they are sent and what action is taken when the battery is low so you should probably review and make your desired changes.

Then enable and start ups-monitor.service:

    # systemctl start nut-monitor
    # systemctl enable nut-monitor

Your logs should show upsmon starting and monitoring the ups.

Category:

- Power management